We have realized an extension of the current steam boiler installation for a large animal feed producer in Genemuiden. The steam capacity of the current steam installation was no longer sufficient for the increased production capacity of the customer.
Replacement of steam boilers
For this reason, one of the existing steam boilers was exchanged for a new 3-pass Viessmann M75C with a capacity of 6 tons of steam per hour at an operating pressure of 13 bar. The installation is controlled by a PLC control. Because the various controls have been implemented in a modulating manner and various heat exchangers have been installed, it has been possible to realize an installation with a high efficiency. For example, the steam boiler has a economizer and a flue gas condenser. With these two heat exchangers, all residual heat from the flue gases is used to heat process water. The modulating feed water control also ensures that the economizer is continuously loaded during operation, which contributes to the high efficiency of the installation.
Installation equipped with Weishaupt gas burner
The installation is equipped with a Weishaupt gas burner in combination with an o² probe. The o² probe contributes to the efficiency of the installation. The burner manager is in fact able to make corrections to the combustion ratios, so that efficient combustion can be guaranteed.
During the exchange of the existing steam boiler for the new one, Kuiper en Zonen BV temporarily placed a mobile steam boiler as a result of which the nuisance could be kept to a minimum for the customer.